|Title||UPS 120V 400VA/240W 4 OUTLETS|
|Company||STACO ENERGY PRODUCTS|
|Datasheet||Download SB-04001 datasheet
|Others parts numbering|
|SB-04002: UPS 230V 400VA/240W 4 OUTLETS|
|SB-06001: UPS 120V 600VA/360W 6 OUTLETS|
|SB-08001: UPS 120V 800VA/480W 6 OUTLETS|
|SB-08002: UPS 230V 800VA/480W 4 OUTLETS|
|SB-10001: UPS 120V 1KVA/600W 6 OUTLETS|
|SB-10002: UPS 230V 1KVA/600W 4 OUTLETS|
|SB-15001: UPS 120V 1.5KVA/900W 6 OUTLETS|
|SB-15002: UPS 230V 1.5KVA/900W 6 OUTLETS|
|SB-06002: UPS 230V 600VA/360W 4 OUTLETS|
|SB-20002: UPS 230V 2KVA/1200W 6 OUTLETS|
Plug your equipment to Battery Backup Outlets on the rear panel of the UPS. NOTE: Make sure that the UPS is powered on to protect all important devices from data loss during power failure. REMARQUE: Assurez-vous que l'UPS est en marche pour protéger tous les dispositifs importants de perte de données lors de panne de courant. CAUTION: NEVER connect a laser printer or scanner to the battery backup outlets of UPS. The equipment may draw significant power to overload the UPS. AVERTISSEMENT: Ne jamais raccorder une imprimante laser ou un scanner pour les prises de sauvegarde batterie de l'onduleur. L'équipement peut exiger beaucoup d'énergie de surcharger le système UPS
The following items are inside the box: UPS unit User manual USB cable software CD Remove the UPS from its package and inspect it for damage that may have occurred during shipping. If any damage is discovered, re-pack the unit and return it to the place of purchase.
Connect one end of the USB cable to PC and the other to the USB port at the rear of the UPS. Download the ViewPower software to your hard drive. Follow onscreen instructions to complete the software installation.
Connect AC power cord to utility power. Then, the UPS will start to charge inside battery. For best result, charge the battery for 6 hours prior to initial use.
UPS Mode UPS Power on AC Mode LCD Description When UPS is powered on, it will enter this mode for 4 seconds. LCD information will be displayed in the following order when LCD is touched. 1. Output voltage 2. Input voltage 3. Load level 4. Battery capacity When overload occurs, alarm will beep every 0.5 second. Alarm will beep every 10 seconds and LCD information will be displayed in the following order when LCD is touched. 1. Output voltage 2. Input voltage 3. Load level 4. Battery capacity When overload occurs, alarm will beep every 0.5 second.When AVR is functioning, icon will flash every second.
When battery level is low, icon will flash.
A Battery backup outlets AC Input C Fuse/Circuit Breaker D USB com port E Cooling fan (1500/2000 models)
icon will flash. NOTE: If backlight shuts off, you may activate it by touching the screen. Remarque: Si le rétro-éclairage s'éteint, vous pouvez l'activer en touchant l'écran.
Fault condition Output short circuited Overload fault Overcharge Bad or severely discharged battery High output voltage fault Over-temperature LCD Solutions Disconnect short-circuited loads and restart the UPS again. Disconnect all output loads and restart the UPS again. Call for service immediately. Please replace the battery. Call for service immediately. 1. Turn off the unit and wait for cooling. 2. Or remove excessive loads and wait for cooling.SPECIFICATIONS
MODEL CAPACITY Input Voltage Output Voltage Regulation Transfer Time Waveform Battery Type & No Charging Time Dimension (DxWxH) Net Weight (lbs) Humidity Noise Level 600VA/360W 120 VAC SB-08001 800VA/480W
10 % (Bat. mode) Typical 2-6 ms Simulated Sine Wave 12V/9Ahx1 6 hours recover to 90% capacity @ 0-40°C non-condensing) Less than 40dB
MODEL Problem Nothing is displayed on LCD panel. Possible Cause The UPS is not on. Solutions Press the power switch again to turn on the UPS. Battery voltage is too Charge the battery at least low. 6 hours. Battery fault. Replace the battery. Power cord loose. Re-plug the power cord. CAPACITY Input Voltage Output Voltage Regulation Transfer Time Waveform Battery Type & No Charging Time Dimension (DxWxH) Net Weight (lbs) Humidity Noise Level 2KVA/1200W 120 VAC 10 % (Bat. mode) Typical 2-6 ms Simulated Sine Wave 2 6 hours recover to 90% capacity @ 0-40°C non-condensing) Less than 40dBThe UPS always on battery mode. The UPS continuously beeps. Backup time too short.
Please check the fault Please check the fault code for the details. for the details. Battery voltage is too Charge the battery at least low. 6 hours. Overload. Remove some unnecessary loads. Before reconnecting equipment, please verify that the load matches the UPS capability specification. Battery defect. Replace the battery.
SAVE THESE INSTRUCTION-This manual contains important instructions that should be followed during installation and maintenance of the UPS and batteries. This UPS utilizes voltage that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts. Only factory service personnel may perform repairs. The utility outlet that supplies the UPS shall be installed near the UPS and shall be easily accessible. During the installation of this equipment it should be assured that the sum of the leakage currents of the UPS and the connected loads does not exceed 3.5mA. Connection to any other type of receptacle other than a twopole, three-wire grounded receptacle may result in shock hazard as well as violate local electrical codes. In the event of an emergency, press the "OFF" button and disconnect the power cord from the AC power supply to properly disable the UPS. Do not allow any liquids or any foreign object to enter the UPS. Do not place beverages or any other liquid-containing vessels on or near the unit. This unit intended for installation in a controlled environment (temperature controlled, indoor area free of conductive contaminants). Avoid installing the UPS in locations where there is standing or running water, or excessive humidity. Do not plug the UPS input into its own output. Do not attach a power strip or surge suppressor to the UPS. Do not attach non-computer-related items, such as medical equipment, life-support equipment, microwave ovens, or vacuum cleaners to UPS. NOTE: This equipment has been tested and found to comply with the limits for a Class A digital device, pursuant to part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference when the equipment is operated in a commercial environment. This equipment generates, uses, and can radiate radio frequency energy and, if not installed and used in accordance with the instruction manual, may cause harmful interference to radio communications. Operation of this equipment in a residential area is likely to cause harmful interference in which case the user will be required to correct the interference at his own expense. WARNING: Changes or modifications not expressly approved by the party responsible for compliance could void the user's authority to operate the equipment. If any abnormal situations occur that are not listed above, please call for service immediately. Do not dispose of batteries in a fire as they may explode. A battery can present a risk of electrical shock and high short circuit current. The following precautions should be observed when working on batteries: 1) Remove watches, rings, or other metal objects from the hands. 2) Use tools with insulated handles. 3) Wear rubber gloves and boots. 4) Do not lay tools or metal parts on top of batteries. 5) Disconnect charging source prior to connecting or disconnecting batteries terminal. Internal battery voltage is 12VDC.Sealed, lead-acid, 6-cell battery. Servicing of batteries should be performed or supervised by personnel knowledgeable of batteries and the required precautions. Keep unauthorized personnel away from batteries. When replacing batteries, replace with the same number and type of sealed lead-acid battery. Do not open or mutilate the battery or batteries. Release electrolyte is harmful to the skin and eyes. It may be toxic. Attention, hazardous through electric shock. Also with disconnection of this unit from the mains, hazardous voltage still may be accessible through supply from battery. The battery supply should be therefore disconnected in the plus and minus pole at the connectors of the battery when maintenance or service work inside the UPS is necessary. To reduce the risk of overheating the UPS, do not cover the UPS' cooling vents and avoid exposing the unit to direct sunlight or installing the unit near heat emitting appliances such as space heater or furnaces. Unplug the UPS prior to cleaning and do not use liquid or spray detergent.
|Some Part number from the same manufacture STACO ENERGY PRODUCTS|